7July 2017; DLO
The electrical outage conducted on the 2nd floor Thursday, July 6, resulted in an unexpected Internet outage for the NMR Lab from 6:15 a.m to 8:48 a.m., an outage that included other parts of CLSLA. The 750NB had to be re-mounted to Samba. Temperature data and dry air data were not acquired during this time interval. An oscilloscope monitoring the 750WB could not be viewed over the Internet starting at 6:15 a.m. It was not fully understood that the Internet closet on the 2nd floor would be affected by the power outage, but it clearly was.
3 July 2017; DLO
An electrical outage is planned on the 2nd floor for 6 to 10 a.m. on Thursday, July 6. Not expected to affect the NMR Lab in A151 CLSL.
14 June 2017; DLO
Last night, the cooling failed in A151. Here are some key observations:
The temperature data for A151 shows a distinct increase at 10:30 p.m. One might guess that something turned off at that time.
The temp increased from 68 F to 82 F from 10:30 p.m. to 4:30 a.m. That’s 14 degrees F in 7 hours.
John Rosheck did us a huge favor by sending an mail to the F & S help desk at 12:05 a.m. I am unaware of any overnight response to this that would have set the heating event to a cooling event about 4:30 a.m.
From about 4:30 a.m. to 6:30 a.m., the temperature recovered to the original 68 degrees F.
John noticed an event in the power monitoring for A151. At about 10:30 p.m., a small drop in the monitored power occurred. At about 4:30 a.m., a small increase occurred. We don’t know that this means. You have to look carefully, but the signature is there. This matter is apparently resolved, but we are not sure exactly what happened our how it could be prevented. Also, we are not sure how it was discovered, as F&S wrote to John and said he had contacted IT, not F&S. An F&S person named Paul Barton thought compressors went off at some point. Times not verified.
5 June 2017; DLO
No special activities planned from this date forward. Any changes will be posted here.